Water: Basic Information about Regulated Drinking Water Contaminants
Basic Information about Disinfection Byproducts in Drinking Water: Total Trihalomethanes, Haloacetic Acids, Bromate, and Chlorite
To protect drinking water from disease-causing organisms, or pathogens, water suppliers often add a disinfectant, such as chlorine, to drinking water. However, disinfection practices can be complicated because certain microbial pathogens, such as Cryptosporidium, are highly resistant to traditional disinfection practices. Also, disinfectants themselves can react with naturally-occurring materials in the water to form byproducts, which may pose health risks.
A major challenge for water suppliers is how to control and limit the risks from pathogens and disinfection byproducts. It is important to provide protection from pathogens while simultaneously minimizing health risks to the population from disinfection byproducts. For more information, see fact sheets on Pathogens and Indicators and Disinfectants.
- What disinfection byproducts does EPA regulate, how are they formed, and what are their health effects in drinking water at levels above the maximum contaminant level?
- What are EPA’s drinking water regulations for disinfection byproducts?
- How will I know if disinfection byproducts are in my drinking water?
- How will disinfection byproducts be removed from my drinking water?
- How do I learn more about my drinking water?
What disinfection byproducts does EPA regulate, how are they formed, and what are their health effects in drinking water at levels above the maximum contaminant level?
|Disinfection Byproduct (Chemical Abstract Service Registry Number)||How is it formed?||Health Effects|
|Bromodichloromethane (75-27-4)||Trihalomethanes occur when naturally-occurring organic and inorganic materials in the water react with the disinfectants, chlorine and chloramine.||Some people who drink water containing total trihalomethanes in excess of the MCL over many years could experience liver, kidney, or central nervous system problems and increased risk of cancer.|
|Dichloroacetic acid (79-43-6)||Haloacetic acids occur when naturally-occurring organic and inorganic materials in the water react with the disinfectants, chlorine and chloramine.||Some people who drink water containing haloacetic acids in excess of the MCL over many years may have an increased risk of getting cancer.|
|Trichloroacetic acid (76-03-9)|
|Chloroacetic acid (79-11-8)|
Dibromoacetic acid (631-64-1)
|Bromate (15541-45-4)||Bromate occurs when bromide in the water reacts with the disinfectant, ozone.||Some people who drink water containing bromate in excess of the MCL over many years may have an increased risk of getting cancer.|
|Chlorite (7758-19-2)||Chlorite occurs when chlorine dioxide breaks down.||Some infants and young children who drink water containing chlorite in excess of the MCL could experience nervous system effects. Similar effects may occur in fetuses of pregnant women who drink water containing chlorite in excess of the MCL. Some people may experience anemia.|
This health effects language is not intended to catalog all possible health effects for disinfection byproducts. Rather, it is intended to inform consumers of some of the possible health effects associated with disinfection byproducts in drinking water when the rule was finalized.
What are EPA’s drinking water regulations for disinfection byproducts?
In 1974, Congress passed the Safe Drinking Water Act. This law requires EPA to determine the level of contaminants in drinking water at which no adverse health effects are likely to occur. These non-enforceable health goals, based solely on possible health risks and exposure over a lifetime, with an adequate margin of safety, are called maximum contaminant level goals (MCLG). Contaminants are any physical, chemical, biological or radiological substances or matter in water. EPA sets MCLGs based on the best available science to prevent potential health problems.
Based on the MCLG, EPA sets an enforceable regulation called a maximum contaminant level (MCL). MCLs are set as close to the health goals as possible, considering cost, benefits and the ability of public water systems to detect and remove contaminants using suitable treatment technologies. MCLs for disinfection byproducts are set at the following levels:
|Levels for Total Trihalomethanes|
|Bromodichloromethane||Zero||0.080 mg/L or 80 ppb
(Sum of the concentrations of all four trihalomethanes) as an annual average
|Dibromochloromethane||0.06 mg/L or 60 ppb|
|Chloroform||0.07 mg/L or 70 ppb|
|Levels for Haloacetic acids|
|Dichloroacetic acid||Zero||0.060 mg/L or 60 ppb
(Sum of the concentrations of all five haloacetic acids) as an annual average
|Trichloroacetic acid||0.02 mg/L or 20 ppb|
|Monochloroacetic acid||0.07 mg/L or 70 ppb|
|Bromoacetic acid||Regulated with this group but has no MCLG|
|Dibromoacetic acid||Regulated with this group but has no MCLG|
|Bromate||Zero||0.010 mg/L or 10 ppb as an annual average|
|Chlorite||0.80 mg/L or 800 ppb||1.0 mg/L or 1 part per million (ppm)|
MCLs are set as close to the health goals as possible, considering cost, benefits and the ability of public water systems to detect and remove contaminants using suitable treatment technologies. States may set more stringent drinking water MCLGs and MCLs for disinfection byproducts than EPA.
The following drinking water regulations apply to disinfectants and disinfection byproducts:
- Stage 1 Disinfectants and Disinfection Byproducts Rule (Stage 1 DBP) (December 16, 1998)
The Stage 1 Disinfectants and Disinfection Byproducts Rule reduces exposure to disinfection byproducts for customers of community water systems and non-transient non-community systems, including those serving fewer than 10,000 people, that add a disinfectant to the drinking water during any part of the treatment process.
- Stage 2 Disinfectants and Disinfection Byproducts Rule (Stage 2 DBP) (December 15, 2005)
Stage 2 DBP rule builds upon earlier rules that addressed disinfection byproducts to improve your drinking water quality and provide additional public health protection from disinfection byproducts.
The Safe Drinking Water Act requires EPA to periodically review the national primary drinking water regulation for each contaminant and revise the regulation, if appropriate, based on new scientific data. EPA will include the Disinfectants and Disinfection Byproducts rules in a future review cycle.
How will I know if disinfection byproducts are in my drinking water?
When routine monitoring indicates that disinfection byproduct levels are above the MCL, your water supplier must take steps to reduce the amount of disinfection byproductsso that they are below that level. Water suppliers must notify their customers as soon as practical, but no later than 30 days after the system learns of the violation. Additional actions, such as providing alternative drinking water supplies, may be required to prevent serious risks to public health.
How will disinfection byproducts be removed from my drinking water?
Water systems that use surface water or ground water under the direct influence of surface water and use conventional filtration treatment are required to remove specified percentages of organic materials that may react with disinfectants to form disinfection byproducts, prior to disinfection. Other control strategies include modification of disinfection practices in a manner that still provides adequate protection against pathogens.
How do I learn more about my drinking water?
EPA strongly encourages people to learn more about their drinking water, and to support local efforts to protect the supply of safe drinking water and upgrade the community water system. Your water bill or telephone book’s government listings are a good starting point for local information.
Contact your water utility. EPA requires all community water systems to prepare and deliver an annual consumer confidence report (CCR) (sometimes called a water quality report) for their customers by July 1 of each year. If your water provider is not a community water system, or if you have a private water supply, request a copy from a nearby community water system.
- The CCR summarizes information regarding sources used (i.e., rivers, lakes, reservoirs, or aquifers), detected contaminants, compliance and educational information.
- Some water suppliers have posted their annual reports on EPA’s website.
Other EPA websites
You will need Adobe Reader to view some of the files in this section. See EPA's PDF page to learn more.
- Find an answer or ask a question about drinking water contaminants on EPA’s Question and Answer website or call EPA’s Safe Drinking Water Hotline at (800) 426-4791
- EPA’s Microbials and Disinfection Byproducts website
- EPA’s Envirofacts ICR website
- EPA’s Guidance Manual Alternative Disinfectants and Oxidants (PDF) (41 pp, 385 K)
- EPA’s Integrated Risk Information System
- EPA History of Drinking Water Treatment (PDF) (4 pp, 156 K)
- EPA Drinking Water Treatment Fact Sheet (PDF) (3 pp, 258 K)
Other Federal Departments and Agencies